# Realistic Expectations and "The Occupied Zone"

How many times as a technician have you gone out to the same customer's home because of unrealistic expectations?  Some homeowners expect air-conditioners to work like an ice box, want you to size them for their big party on Fourth of July weekend, and expect you to show up at the drop of a dime when it doesn't meet their impossible notion.  Of course, this could be avoided by establishing a standard during the sales process or a little customer education.  I liked to talk about "The Occupied Zone" and work in a little Radiant Asymmetry, using more layman's terms of course.

 Occupied Zone - ACCA Manual RS

The occupied zone is a concept used in the design process to properly heat and cool spaces without a customer feeling drafts.  As you can see in the picture taken from ACCA Manual RS: Comfort, Air Quality, and Efficiency By Design, the zone is 2' inwards from all walls and ceilings.  ACCA Manual J: Residential Load Calculation, states the occupied zone is only 6.5' in height.  This area near walls and ceilings is use to mix conditioned air with room air.  In fact, this mixing is what cuts down on occupants feeling convective currents or drafts in the heating season.

 ASHRAE Standard 55

Not only will occupants feel drafts, but they will feel what is termed as radiant asymmetry.  This is the phenomenon (not really, just to a homeowner) of a warm or cold temperature.  If the wall is colder than you are, the wall will be pulling radiant heat from you.  This makes you feel cold, even if it is 70F in the room, hence the statement "a cold 70F".  The best example I ever heard of this is the temperature at an ice rink.  It feels cold when on the ice, but the air temperature hovers around 65F!  Anyhow, have you ever wondered how much asymmetry is too much?  ASHRAE Standard 55: Thermal Environmental Conditions for Human Occupancy was nice enough to spell this out for us.  As you can see, a warm ceiling is the number one device that occupants will find uncomfortable with only a 10-20F difference.  This would of course happen during the cooling season, and with any luck on Friday afternoon just before that Summer, holiday weekend/family reunion, right?  I can see this happening more often in Cape style homes since there are more ceiling/roof combinations and occupants are more than likely outside of the occupied zone.  The only answer to this issue is proper home air sealing and insulation.  It does not matter how oversized your air-conditioner is, it will not be able to overcome the laws of physics and radiation.  This is just another reason to peer into the attic during your sales calls to verify the weatherization of the home and the thermal boundary.  Don't set your install up for failure, and certainly establish some basic expectations with the homeowner.  You don't want to leave this up to your technician on a holiday weekend, getting paid double-time for warranty work!

http://excessair.blogspot.com/2012/05/realistic-expectations-and-oc...

Views: 582

Comment

Join Home Energy Pros Forum

Comment by Bob Blanchette on May 14, 2012 at 8:16pm

Contractors need to discuss humidity control and how going with a huge A/C unit will make the house feel muggy. Also temperature swings and noise levels should be mentioned. Comfort is not just about maintaining a certain setpoint regardless of conditions.

## Forum Discussions

### Beginners Guide: Managing Subscriptions on Home Energy Pros

Started by David Butler in General Forum yesterday.

### Welcome Home Performance Forum Members! (formerly RESNET BPI - Energy Audit and Home Performance)

Started by David Butler in General Forum yesterday.

### Speed Tips For Duct Airtightness Testing?

Started by Brendan Reid in General Forum. Last reply by David Butler yesterday.

### What made this chimney fall down?

Started by Eric Kjelshus in General Forum. Last reply by Eric Kjelshus Nov 13.

### How would you insulate this roof?

Started by David Butler in General Forum. Last reply by Dave Taylor Nov 11.

205 members

73 members

71 members

27 members

74 members

## Latest Activity

Dara Bowser replied to Don Fugler's discussion joining ducts in the group HVAC
"Good to hear you have clean dryer ducts Don. The dryer duct issues that we run into are…"
12 hours ago
Don Fugler replied to Don Fugler's discussion joining ducts in the group HVAC
"David, If the IMC mandates metal dryer duct and prohibits metal screws, they must be accepting…"
13 hours ago
David Butler replied to Don Fugler's discussion joining ducts in the group HVAC
"I never checked that before. Checking now... Section M1502.4.2 of the International Residential…"
13 hours ago
Joseph Frasier is now a member of Home Energy Pros Forum
13 hours ago
Don Fugler replied to Don Fugler's discussion joining ducts in the group HVAC
"Brendan, Thanks for that response. Because of your warning, I just went down to the basement and…"
17 hours ago
Brendan Reid replied to Don Fugler's discussion joining ducts in the group HVAC
"Hi Don, Summary: DRYER VENT: screws bad idea, possibly prohibited by code. METAL DUCT: must be…"
17 hours ago
Brendan Reid and David Butler joined Allison A. Bailes III's group

### HVAC

HVAC design, Manuals J, S, T, & D, Duct leakage, Air flow, ENERGY STAR new home requirements,…See More
17 hours ago
Sean Wiens and David Butler joined Chris Laumer-Giddens's group

### Energy Efficient Design

Energy efficiency starts at the drafting table...How architects and designers can help buildings…See More
yesterday