# Duct Gains: Why do we hate R-8?

Ever since the adoption of the 2009 International Residential Energy Conservation Code (IECC), duct sealing efforts have been tested using the total leakage or leakage to outdoors methods.  It really is amazing how much duct gains effect the operation of your equipment and the comfort of your customer.  The missing part of "duct testing" appears to be how well the ducts are insulated.  Sure, you are required to use R-8 insulation on supply ductwork when located outside the building envelope, but how do we know it was installed correctly?  We're not required to test like the duct leakage codes, so is a check in the box sufficient?  How about we use some simple math to figure the gains, or lost capacities in cooling, and hold everyone to a standard - check out the equation below.

Sensible Btu/hr = CFM x Delta T x 1.08
So, based on this math, one can take a few simple temperature measurements and calculate the lost sensible capacities due to duct leakage and insulation.   You should measure the temp of the air entering the return grille and at the unit to figure the return gain in sensible temperature.  I would also recommend averaging the temp readings at the furthest supply register, an average supply register, and a close one to figure the delta T from the air exiting the coil or air handler.  Do the same for an extensive return system.

When you start measuring, it is very scary what you start to find.  As you can see, like the industry accepted national average, this system is losing 30% of the 3-ton capacity through it's well sealed, but poorly insulated duct system.  Unfortunately, the method is not perfect since a hotter day in the attic could cause greater gains.  But, that would be the time to sell duct sealing and insulation to the homeowner!  Any of you energy auditors out there could probably comment on how much attic ducts effect home infiltration as well.  So, why do we hate R-8 insulation?  Is it really just the hassle of wrapping the equivalent of a blanket around the ducts?  I don't recommend retrofitting a distribution system in an attic in the middle of July, but maybe it makes sense to offer to come back in the Fall?  Please, don't just leave it be!  Doing so makes it hard for this tree hugger to sleep at night!

http://excessair.blogspot.com/2012/06/duct-gains-why-do-we-hate-r-8...

Views: 1592

Comment

Join Home Energy Pros Forum

Comment by Bob Blanchette on June 29, 2012 at 9:44pm

The best bet is to reduce duct surface area if you can't get the ductwork into conditioned space. Have fewer registers and larger ductwork instead of lots of registers with small ductwork. Use truck/branch instead of '"ductopus". Keep runs short as possible. Eliminate runs to small/lightly used spaces. Put registers on sidewalls closer to the air handler, set sidewall registers to blow out into room.

The return isn't as big of an offender as the supply. As long as return is tightly sealed the wetbulb temperature won't change much. Wetbulb determines evaporator load. Then there is doing what you can to reduce attic temps, the best solution is typically large area passive vents. If you can see light coming through while in the attic, it's working...

## Forum Discussions

### Beginners Guide: Managing Subscriptions on Home Energy Pros

Started by David Butler in General Forum yesterday.

### Welcome Home Performance Forum Members! (formerly RESNET BPI - Energy Audit and Home Performance)

Started by David Butler in General Forum yesterday.

### Speed Tips For Duct Airtightness Testing?

Started by Brendan Reid in General Forum. Last reply by David Butler yesterday.

### What made this chimney fall down?

Started by Eric Kjelshus in General Forum. Last reply by Eric Kjelshus Nov 13.

### How would you insulate this roof?

Started by David Butler in General Forum. Last reply by Dave Taylor Nov 11.

205 members

73 members

71 members

27 members

74 members

## Latest Activity

Dara Bowser replied to Don Fugler's discussion joining ducts in the group HVAC
"Good to hear you have clean dryer ducts Don. The dryer duct issues that we run into are…"
7 hours ago
Don Fugler replied to Don Fugler's discussion joining ducts in the group HVAC
"David, If the IMC mandates metal dryer duct and prohibits metal screws, they must be accepting…"
8 hours ago
David Butler replied to Don Fugler's discussion joining ducts in the group HVAC
"I never checked that before. Checking now... Section M1502.4.2 of the International Residential…"
9 hours ago
Joseph Frasier is now a member of Home Energy Pros Forum
9 hours ago
Don Fugler replied to Don Fugler's discussion joining ducts in the group HVAC
"Brendan, Thanks for that response. Because of your warning, I just went down to the basement and…"
13 hours ago
Brendan Reid replied to Don Fugler's discussion joining ducts in the group HVAC
"Hi Don, Summary: DRYER VENT: screws bad idea, possibly prohibited by code. METAL DUCT: must be…"
13 hours ago
Brendan Reid and David Butler joined Allison A. Bailes III's group

### HVAC

HVAC design, Manuals J, S, T, & D, Duct leakage, Air flow, ENERGY STAR new home requirements,…See More
13 hours ago
Sean Wiens and David Butler joined Chris Laumer-Giddens's group

### Energy Efficient Design

Energy efficiency starts at the drafting table...How architects and designers can help buildings…See More
21 hours ago