# Duct Gains: Why do we hate R-8?

Ever since the adoption of the 2009 International Residential Energy Conservation Code (IECC), duct sealing efforts have been tested using the total leakage or leakage to outdoors methods.  It really is amazing how much duct gains effect the operation of your equipment and the comfort of your customer.  The missing part of "duct testing" appears to be how well the ducts are insulated.  Sure, you are required to use R-8 insulation on supply ductwork when located outside the building envelope, but how do we know it was installed correctly?  We're not required to test like the duct leakage codes, so is a check in the box sufficient?  How about we use some simple math to figure the gains, or lost capacities in cooling, and hold everyone to a standard - check out the equation below.

Sensible Btu/hr = CFM x Delta T x 1.08
So, based on this math, one can take a few simple temperature measurements and calculate the lost sensible capacities due to duct leakage and insulation.   You should measure the temp of the air entering the return grille and at the unit to figure the return gain in sensible temperature.  I would also recommend averaging the temp readings at the furthest supply register, an average supply register, and a close one to figure the delta T from the air exiting the coil or air handler.  Do the same for an extensive return system.

When you start measuring, it is very scary what you start to find.  As you can see, like the industry accepted national average, this system is losing 30% of the 3-ton capacity through it's well sealed, but poorly insulated duct system.  Unfortunately, the method is not perfect since a hotter day in the attic could cause greater gains.  But, that would be the time to sell duct sealing and insulation to the homeowner!  Any of you energy auditors out there could probably comment on how much attic ducts effect home infiltration as well.  So, why do we hate R-8 insulation?  Is it really just the hassle of wrapping the equivalent of a blanket around the ducts?  I don't recommend retrofitting a distribution system in an attic in the middle of July, but maybe it makes sense to offer to come back in the Fall?  Please, don't just leave it be!  Doing so makes it hard for this tree hugger to sleep at night!

http://excessair.blogspot.com/2012/06/duct-gains-why-do-we-hate-r-8...

Views: 1592

Comment

### You need to be a member of Home Energy Pros Forum to add comments!

Join Home Energy Pros Forum

Comment by Bob Blanchette on June 29, 2012 at 9:44pm

The best bet is to reduce duct surface area if you can't get the ductwork into conditioned space. Have fewer registers and larger ductwork instead of lots of registers with small ductwork. Use truck/branch instead of '"ductopus". Keep runs short as possible. Eliminate runs to small/lightly used spaces. Put registers on sidewalls closer to the air handler, set sidewall registers to blow out into room.

The return isn't as big of an offender as the supply. As long as return is tightly sealed the wetbulb temperature won't change much. Wetbulb determines evaporator load. Then there is doing what you can to reduce attic temps, the best solution is typically large area passive vents. If you can see light coming through while in the attic, it's working...

## Forum Discussions

### What made this chimney fall down?

Started by Eric Kjelshus in General Forum. Last reply by Eric Kjelshus on Tuesday.

### How would you insulate this roof?

Started by David Butler in General Forum. Last reply by Dave Taylor Nov 11.

### Manual J (SD) for custom, luxury homes

Started by Dav Camras in HVAC. Last reply by Dav Camras Nov 10.

### Quantitative methods for residential zoning

Started by Brett in HVAC. Last reply by David Butler Nov 9.

### Home Energy Pros and #MeToo

Started by Mike Rogers in General Forum. Last reply by Mike Rogers Nov 9.

304 members

133 members

332 members

1 member

26 members

## Latest Activity

Sonny Roncancio and Chester Energy &amp; Policy joined Home Energy Pros Forum
11 hours ago
Ryan Moore updated an event

### LEED for Homes Green Rater Training at Fort Collins, CO

December 7, 2017 to December 8, 2017
Green Insight will host this 2-day training in Fort Collins, CO December 7-8,…See More
yesterday
Rodney Bailey liked Rodney Bailey's discussion Energy audit equipment for sale.
yesterday
yesterday
Home Energy Magazine's blog post was featured

### People Who Save Energy

Wednesday
Home Energy Magazine posted a blog post

### People Who Save Energy

Wednesday
Quinn Korzeniecki added a discussion to the group Building Performance Institute (BPI)

### Rebates and Incentives: Illinois

Curious about home performance incentives and rebates available in your area? Check out this BPI…See More
Wednesday
Stacey Cordeiro and Melissa Ames joined Home Energy Pros Forum
Wednesday

## Photos

• Add Photos
• View All

© 2017   Created by Home Performance Coalition (HPC)   Powered by