# Target superheat formula

You said take wet bulb at unit not in the house am i right or did i miss understand the formula

Views: 5419

### Replies to This Discussion

You take the Indoor Wet Bulb and the Outdoor Temp

Thank You
Can you explain this superheat formula like way do we times it by 3 and mines 80 and mines cond enterning ambient,.

Thanks Mike O

Target SH = [(3 x indoor wb) - 80 - ambient] / 2 (°F)

Usually, if you are charging an ac , the manufacturer gives you a superheat range they want the equipment to operate at  (usually 6-8 degrees)   The higher the wetbulb the more capacity/cooling will be diverted to removing moisture/humidity.

The super heat will show if the TXV is operating correctly as well.  It is a great tool for diagnosis.  If you are an HVAC dealer, your equipment manufacturer rep will be happy to explain it all to you.

All the various scenarios are to involved to train someone here.

Yikes -- Folks help me out. I am confused. As I recall, the target superheat for a fixed metering device (orifice/non-TXV) is dependent on the return plenum wet bulb (at the plenum, not in the house because what the air conditioner sees is what is in the return plenum, not necessarily the same as the wet bulb in the house) and the condenser air entering temperature.

I checked the formula given against the generic table (originally Carrier) and found the formula proposed is way off (not usable). I gets vastly the wrong answer under many scenarios. For example at 58 return plenum WB and 80 condenser air entering temperature it gives a target superheat of 34F, while the standard table gives a target of less than 5F.

Check out the linked table below from the California Title 24 Standards

On the other hand a TXV is a constant superheat valve -- so it should not change with different return plenum or outdoor conditions. For adjustable TXVs some experienced people (like Rick Chitwood) adjust it to 6 degrees F system superheat (system superheat is based on the temperature of the suction line as it enters the outdoor unit on split systems). For a TXV or EXV it is often not adjustable, but you should suspect a problem if it is high (approx15 F or above) or low (less than 3F).

Attachments:

## Discussion Forum

### REMRATE Modeling of 2 stage Heat Pumps - Including GSHP

Started by Jeremy Begley. Last reply by David Butler May 16.

### Manual S for Water Furnace Equipment

Started by Jeremy Begley. Last reply by Danny Gough Mar 23.

### joining ducts

Started by Don Fugler. Last reply by Dara Bowser Nov 28, 2017.

### HVAC integration – the past, the present, and the future

Started by Igor Mitbarg. Last reply by Lucifer Prescott Apr 11, 2017.

### Efficient furnace with maximum temperature

Started by Thaara Mar 30, 2016.

19 members

40 members

137 members

152 members

56 members

## Latest Activity

Sean Wiens posted a discussion

### Outdoor Reset

Can some of you weigh in on what you feel is the best wired outdoor reset and why?  I am currently…See More
7 hours ago
Tom Phillips replied to Don Fugler's discussion Choosing a range hood in the group Kitchen Ventilation
"thx Don! re: Capture Efficiency, the ROÇIS Kitchen Range Hood document addresses what hood…"
12 hours ago
Dara Bowser joined Don Fugler's group

### Kitchen Ventilation

In many homes, cooking is the largest indoor source of air pollutants. Exposures can be higher in…See More
12 hours ago
Dara Bowser liked Don Fugler's discussion Choosing a range hood
13 hours ago
Chris Hawkins and Drew Brauer joined Home Energy Pros Forum
yesterday
Lauren Asplen and Danny Gough joined Bob Krell's group

### Healthy Indoors (IAQ)

The Healthy Indoors group is focused on indoor air quality (IAQ), mold, moisture control, radon,…See More
yesterday
"Is strongly advise against attempting to install any complex home comfort equipment on your own.…"
yesterday
CEE posted a blog post

yesterday

### A Climate Report From The Field - Dave Keefe

yesterday
Julie Saporito's blog post was featured

### Denver Announces Pilot Program to Raise Awareness of Energy Costs in Homes

yesterday
yesterday
John Walter and Eric Rabesa joined Home Energy Pros Forum
Thursday
William Collins posted a video

### The Foam Sealants Kit " Bead or Spray"

Now you can apply foam sealant as a " bead " or a " spray " with the Foam Sealants Kit. When using a 16lb Canister of Black Sealant you can easily go from us...
Thursday
Sean Wiens and Armando Cobo joined Don Fugler's group

### Kitchen Ventilation

In many homes, cooking is the largest indoor source of air pollutants. Exposures can be higher in…See More
Thursday
Julie Saporito posted a blog post

### Denver Announces Pilot Program to Raise Awareness of Energy Costs in Homes

Thursday
"Cook outside, as much as you can, and close your doors/windows while you do it ;) "
Thursday
Ethan Foley joined Bob Krell's group

### Healthy Indoors (IAQ)

The Healthy Indoors group is focused on indoor air quality (IAQ), mold, moisture control, radon,…See More
Thursday
Shane S posted a photo

### House rewiring Melbourne

Thursday
Al Tibbs posted photos
Wednesday

### IMG00173-20100805-1030

"Always remind customer to make sure to mark out location of piping before covering!! The infrared…"
Wednesday