# Target superheat formula

You said take wet bulb at unit not in the house am i right or did i miss understand the formula

Views: 6027

### Replies to This Discussion

You take the Indoor Wet Bulb and the Outdoor Temp

Thank You
Can you explain this superheat formula like way do we times it by 3 and mines 80 and mines cond enterning ambient,.

Thanks Mike O

Target SH = [(3 x indoor wb) - 80 - ambient] / 2 (°F)

Usually, if you are charging an ac , the manufacturer gives you a superheat range they want the equipment to operate at  (usually 6-8 degrees)   The higher the wetbulb the more capacity/cooling will be diverted to removing moisture/humidity.

The super heat will show if the TXV is operating correctly as well.  It is a great tool for diagnosis.  If you are an HVAC dealer, your equipment manufacturer rep will be happy to explain it all to you.

All the various scenarios are to involved to train someone here.

Yikes -- Folks help me out. I am confused. As I recall, the target superheat for a fixed metering device (orifice/non-TXV) is dependent on the return plenum wet bulb (at the plenum, not in the house because what the air conditioner sees is what is in the return plenum, not necessarily the same as the wet bulb in the house) and the condenser air entering temperature.

I checked the formula given against the generic table (originally Carrier) and found the formula proposed is way off (not usable). I gets vastly the wrong answer under many scenarios. For example at 58 return plenum WB and 80 condenser air entering temperature it gives a target superheat of 34F, while the standard table gives a target of less than 5F.

Check out the linked table below from the California Title 24 Standards

On the other hand a TXV is a constant superheat valve -- so it should not change with different return plenum or outdoor conditions. For adjustable TXVs some experienced people (like Rick Chitwood) adjust it to 6 degrees F system superheat (system superheat is based on the temperature of the suction line as it enters the outdoor unit on split systems). For a TXV or EXV it is often not adjustable, but you should suspect a problem if it is high (approx15 F or above) or low (less than 3F).

Attachments:

## Discussion Forum

### REMRATE Modeling of 2 stage Heat Pumps - Including GSHP

Started by Jeremy Begley. Last reply by David Butler May 16, 2018.

### Manual S for Water Furnace Equipment

Started by Jeremy Begley. Last reply by Danny Gough Mar 23, 2018.

### joining ducts

Started by Don Fugler. Last reply by Dara Bowser Nov 28, 2017.

### HVAC integration – the past, the present, and the future

Started by Igor Mitbarg. Last reply by Lucifer Prescott Apr 11, 2017.

### Efficient furnace with maximum temperature

Started by Thaara Mar 30, 2016.

338 members

45 members

173 members

37 members

33 members

## Latest Activity

"I've been waiting for this show to release! Corbett always is worth a watch. Check out his…"
12 hours ago
Maria M Hernandez and Robert Corbyn joined Home Energy Pros Forum
14 hours ago
Diane Chojnowski posted a discussion

### Home Diagnosis Episode 2: Environmental Sensitivity and Healthy Homes

Check this out! You can watch Episode 2 of Home Diagnosis on PBS or on YouTube.Episode 2 visits a…See More
15 hours ago
"Hi Diane, This looks like a great event! Please post it on our event calendar and we'll share…"
15 hours ago
Robert Corbyn posted photos
15 hours ago
"Life means many things, but besides taking care of your family, home and working, you should take…"
18 hours ago
"Interesting. Something needs to change when 30% of the exemplary programs (16 out of 53) saw…"
yesterday
Dimitri Mal joined Bob Krell's group

### Healthy Indoors (IAQ)

The Healthy Indoors group is focused on indoor air quality (IAQ), mold, moisture control, radon,…See More
yesterday