# Transient Heat Transfer Analysis

I have put together an Excel spreadsheet that calculates the temperature profile through a wall that is heated by the sun.

It use the matrix [K]{T} + [C]{dT/dt} = {S}, where [K] is the heat transfer, {T} is the temperature at the various nodes, [C] is the thermal capacitance of the node, and {S} is the thermal heat gain of the outer node. A copy of the spreadsheet and matrix math is attached.

The math equations have not been verified for accuracy or errors, but it is kind of fun to play around with the variables to see how the temperature profile in the wall changes throughout the day.

(Note that an earlier version of this post had the attached Excel file as a *.zip file.  It has been replaced with an Excel version.)

Views: 2142

Attachments:

### Replies to This Discussion

Does this assume that all the heat the face is not leaving, or does it account for convetive currents on the face taking some heat away? Does it assume no wind? What boundry factors have you set up?

The spreadsheet calculates whether heat is going in or out.  Yes, it accounts for convective currents removing heat from the surface.  You can specify any interior or interior convective heat transfer coefficients or air temperatures that you want.  You can also specify the amount of solar gain that the wall receives based on the absorption coefficient.  A perfectly black surface would absorb all of the solar heat (Absorbtivity = 1.0) and a perfectly reflective surface would have zero absorbtivity. I used it recently to model the heat transfer in and out of cold storage rooms that is kept at 32F.

I'm working on an updated model that provides the thermal properties for different building materials and different convective heat transfer coefficients for wind, no wind, surface orientation etc.

In addition to calculating the heat flow through walls, the spreadsheet could also be used to calculate how quickly the outside of your coffee cup would warm up after filling it with coffee.

This is a nice graphic.  I have a question on how you captured the data -- did you set temperature probes at increasing depths into the brick wall, or are these extrapolated from the delta between interior and exterior temperatures?  Thank you.

The values are all calculated for each node based on the physical characteristics that are input into the model.

To, Ti, hi and ho are inside and outside temperatures and convective heat transfer coefficients,

K is the Conductance (Conductivity/Thickness) of each layer

ρ is the layer's density, and

Cp is the specific heat of the material.

Attached is a detailed description of how I derived the calculations that are used in this transient heat transfer analysis.

Attachments:

## Discussion Forum

### Energy 2D and 3D

Started by James White. Last reply by James White Nov 6, 2014.

### Transient Heat Transfer Analysis

Started by James White. Last reply by James White Dec 10, 2013.

### Trying to find %age energy saving from variety of upgrades in 10K sf multifamily house

Started by George M. Matthews. Last reply by Guy DuBois Mar 18, 2013.

### Using Average Monthly Temperature to Model Home Energy Use

Started by James White. Last reply by James White Dec 28, 2012.

### How about simulation in the multifamily context?

Started by Evan Mills. Last reply by Don Hynek Jan 23, 2012.

314 members

54 members

136 members

12 members

151 members

## Latest Activity

"That's an interesting perspective but it begs certain questions.  Yes, if we were to…"
3 hours ago
"I sent you a friend request so we can communicate directly."
6 hours ago
"Within the US and I would need to add shipping cost.  Where are you located?"
10 hours ago
"I posted an explanation to Liam weeks ago.   Since different LED manufacturers may use…"
yesterday
"No one replied! ."
yesterday
"Are you willing to ship?"
yesterday
Kevin Jacks joined allen p tanner's group

### Energy Auditing Equipment for Sale, Trade or to Purchase

Discuss the pros and cons of the equipment you are interested in prior to purchase. Post equipment…See More
yesterday
"Do not be fooled it is very common problem for cast iron wood working equipment to sweat and rust…"
yesterday
"Most all residential buildings are built with a 50-year life cycle. If the building stock in…"
Saturday
Taylor Joseph Mckay and Karin Haerter joined Home Energy Pros Forum
Friday
"Dave I am selling everything as one package"
Friday
"What's your price for the DM2?"
Friday
"There is no one-size-fits all answer...It would be interesting to see some real data on low income…"
Thursday
"For condensation you need one simple condition. A surface below the dew point. There are lots of…"
Thursday
Thursday
Mick Lane replied to Mark Furst's discussion Worst boiler ever?
"Nice.  Probably want to clean the orifices on the burner. That firebox is a little too full of…"
Thursday
Home Energy Magazine's video was featured

### Legends of Home Performance: Sam Rashkin, Chief Architect, Building Technologies Office, U.S. Department of Energy

Home Energy Magazine's series "Legends of Home Performance". "There's reason for us to be excited from environmental, economic, health perspectives, for the ...
Thursday
Diane Chojnowski added 2 discussions to the group News & Announcements
Thursday
Ron Piethe and Ali Alajmi joined Home Energy Pros Forum
Thursday
"I agree that checking for combustion spillage is more important that checking for draft.  It…"
Thursday