# Fun with Neutral Pressure Planes (NPP)

Greetings

First of all......

* As we upgrade and build new....

I think it is time to eliminate atmospherically vented appliances from the breathing zones of our homes

* I realize that the effects of wind and mechanical equipment can and often do overwhelm Stack Effect.

My current favorite online resources for visualizing "Stack Effect" are.....

*John Straube's Article

http://www.buildingscience.com/documents/digests/bsd-014-air-flow-c...

*John Klote's Article

http://fire.nist.gov/bfrlpubs/fire91/PDF/f91013.pdf

*Bud Poll's Worksheet

I plan to post some Illustrations and see if you folks agree with my current thinking about the location of Neutral Pressure Planes

Meanwhile...

Does anyone else have suggestions for online links concerning  "Stack Effect"?

Views: 5516

### Replies to This Discussion

An important element of the Klote report is that he uses a simplifying formula that only approximates the typical multiple vertical opening model.

"Analytic equations have been developed for the location of the neutral pressure plane for a few simple cases of leakage openings. However, the combinations of leakage openings in building shafts and compartments can be very complex... Analysis is simpler for horizontal openings, because the pressure difference across the opening does not vary with elevation. The analysis of this section is for horizontal openings…Vertical vents can be approximated by horizontal vents when the height of each vent is small compared to the height of the air column."

In a 2500 SF house with 1 ACH50 (about 350 CFM50), the Effective Leakage Area (ELA @ 4 Pa) is about 8 square inches. Since the blower door test is conducted with deliberate leaks sealed, this envelope leakage area is similar to what we might expect from dampered mechanical openings, making both deliberate and accidental leakage areas equally significant.

I'm still not sure what you're trying to accomplish by "controlling" the height of the NPP, especially given that - as you attest - the actual NPP will vary with both wind and mechanical effects.

Here's another link to an old article, CBD-23. Air Leakage in Buildings, from the National Research Council of Canada:

http://archive.nrc-cnrc.gc.ca/eng/ibp/irc/cbd/building-digest-23.html

## Forum Discussions

### How would you insulate this roof?

Started by David Butler in General Forum. Last reply by Brad Cook 4 hours ago.

### Tankless Water Heaters... has their time finally come?

Started by Bob Blanchette in General Forum. Last reply by tedkidd yesterday.

### Psychrometric Chart Training

Started by John Krochmalny in Training. Last reply by Mahendra Shah on Friday.

### Too many Heat Pump Water Heaters in a basement?

Started by Brad Cook in General Forum. Last reply by Crista on Thursday.

### Dirty solar panels

Started by Evan Mills in General Forum. Last reply by Stacie Bagnasco Oct 16.

343 members

162 members

148 members

332 members

25 members

## Latest Activity

"Bill, you just posted a number of responses in different areas of the thread. I will try to respond…"
4 hours ago
4 hours ago
Alice Quinn and Donald Hester joined Home Energy Pros Forum
4 hours ago
"In an earlier response, I noted that we COULD haul drinking water and use the water we collect off…"
4 hours ago
"As to the elevations on the cupola – the existing windows up there might survive adding…"
4 hours ago
"The purlins are 1 3/4" thick. I believe the top chord of the trusses are 10" deep (but…"
4 hours ago
"The cupola windows are the only place there would be a problem if 4" of foam were added above…"
4 hours ago
"The purlins are 1 3/4" thick. I don’t know about the fire dangers of PIC or other foams.…"
4 hours ago