Here you go, dudes:
7.5 cfm per person + 3 cfm per 100 sq. ft. CFA MINUS
[ 1000 x ELA x (H/8.2)ˆ0.4 x WSF ] / 7.3
Tags: 62.2, 62.2-2013, ashrae, calculation, sizing, ventilation
▶ Reply to This
Thanks, Corbett. Another successfully simple and succinct explanation. Good work.
Welcome toHome Energy Pros Forum
Sign Upor Sign In
Or sign in with:
Started by Bob Reuther in Best Practices. Last reply by Daniel Baur-McGuire 9 hours ago.
Started by David Holtzclaw in General Forum. Last reply by William H Nickerson on Thursday.
Started by Quinn Korzeniecki in General Forum Jun 12.
Started by Diane Chojnowski in General Forum Jun 11.
Started by Matthew Mauriello in Infrared Jun 10.
© 2018 Created by Home Performance Coalition (HPC)
Report an Issue |
Terms of Service
Please check your browser settings or contact your system administrator.