Here you go, dudes:
7.5 cfm per person + 3 cfm per 100 sq. ft. CFA MINUS
[ 1000 x ELA x (H/8.2)ˆ0.4 x WSF ] / 7.3
Tags: 62.2, 62.2-2013, ashrae, calculation, sizing, ventilation
▶ Reply to This
Thanks, Corbett. Another successfully simple and succinct explanation. Good work.
Welcome toHome Energy Pros Forum
Sign Upor Sign In
Or sign in with:
Started by Tim Kendzia in General Forum. Last reply by Franco Oyuela yesterday.
Started by Classic Residential, Inc. in General Forum. Last reply by Franco Oyuela yesterday.
Started by David Byrnes in General Forum. Last reply by Franco Oyuela on Monday.
Started by Evan Mills in General Forum. Last reply by Daniel Baur-McGuire on Thursday.
Started by Jerry Needham in General Forum. Last reply by Daniel Baur-McGuire Dec 6.
© 2018 Created by Home Performance Coalition (HPC)
Report an Issue |
Terms of Service
Please check your browser settings or contact your system administrator.